Shenzhen Daceen Technology Co., Ltd.
Shenzhen Daceen Technology Co., Ltd.
Model No.: 12V AnyPulse BPS
Type: On-line With Battery
Protection: Over-Floating Voltage, Cell Capacity Equalization
Application: Telecommunications Base Site Backup Battery Bank
Standby Time: Long-Acting System And Device
Equipment Mode: Decentralized
Monitoring Alarm: Voltage, Current
Max Power Consumption: ≤11,5W
Battery Pack Type: 48V/36AH-300AH In Series By 4 Cells
Place of Origin: SHENZHEN, CHINA
Supply Ability: 36000PCS/Year
Certificate: CE, REACH,ROHS,ISO
HS Code: 8536300000
This device of 12V Stationary Battery Protector System is the Smart Stationary Battery Pulse Maintainer for 48V battery pack in series by 4PCS 12V cells. It is working as a new generation of high-tech products for daily battery maintenance and battery equalization in sites or other stationary power system. 12V Telecom Base Site Battery Protect System, it is designed for the charging maintenance and life extension of new batteries in Telecommunication base sites, or used after our Off line Battery Smart Pulse Repair System restored as 12V Battery Restore System. We also call it as well as on line Battery Smart Pulse Maintainer for its long-term work in parallel at the battery, the sulfated crystals can be effectively removed, and prevent the new sulphation re-buildup. The battery capacity is significantly maintained as new one for long time.It is well known that Telecom service providers have designed the traditional wire-line telecom and wireless network systems for high service availability, its reliability depends on the availability of power from the stationary battery bank in base sites and UPS system standby in operation office. But there must be individual differences in state-of-capacity (SOC) and internal resistance(IR) Value of batteries after used for a certain number of years even if common Battery Care Program is carried out. It is called the battery un-equalization. Due to the total floating charge voltage of the rectifier remains unchanged and keeps constant, when the battery pack is always in floating charging status, the floating voltage of the cells with larger IR will be higher than that of the normal battery, resulting in the normal battery's floating voltage is lower.
Batteries floating charged in this unbalancing way for a long time without Base Site Battery Protector System or Stationary Battery Pulse Equalizer, that will cause the higher voltage cells seriously dehydrated, and the lower voltage cell is in a state of under-charged. This way of vicious spiral formed will accelerate the base site batteries premature sulfation and early failure.
This 12V telecom base site Battery Smart Pulse Protector set a equalized charging function. If the terminal floating voltage of the battery system is higher than the standard value of protector system designed, the system automatically and smartly switches to the over-voltage balanced working state. When the voltage drops lower than standard value, it automatically changes to Stationary Battery Pulse Maintainer state. The decrease of battery IR and the improvement of the battery equalization lead to the battery life extension doubled or more.
It is used for 48V/36AH-300AH battery bank series by 4 PCS 12V/36AH-300AH Lead Acid Cells.
It is only used for the Maintenance and Life extension of new batteries in Telecom Base site, or used after repaired by our off-line Battery Repair System.
Prohibit the use of aged batteries in the absence of being repaired. Once the violation, it may not reach your expectations.
ELECTRICAL PARAMETERS (Pulse Maintenance Status)